Busy week fault finding various jobs but the last one of yesterday was interesting 😀 We were called in following another trade completing a bathroom makeover, with issues getting the mirror to work and repeatedly blowing fuses on the isolation switch... upon further investigation we found what seemed to be the problem, they had used a Wago (a connector block) but not understood it and connected all the Live, Neutral & Earth wires together! Resolved by jointing correctly, but they had also done the same behind the mirror. A new fused isolator installed, jointed correctly and tested, left safe and working. Happy/relieved client....just a shame about the trunking they used to hide the cable 🙄!!